Hi, Every Body. To connect and control PLC by HMI, you need making a connection (communication) PLC and HMI (set by the software and link by a cable). Today, I guide you the step by step to do it. The example in this post: connect PLC S7-200 and Delta HMI DOP-B (B07S411). The other PLCs & HMIs, you can do it with the same method.
Table of Contents
Select the method for connect PLC and HMI
By reading the catalogue and checking the support connection of PLC & HMI use in your project. If it not support, you must change PLC type (or HMI type) to connect PLC and HMI
The example: I read the connection guide for Delta HMI DOP-B (“DOP Series HMI Connection Manual”). The document shows you, the methods connect DOP HMIs & PLCs (RS232, RS485…). Some devices may support Ethernet connection. Find your PLC type use (ex: S7-200).
-> I choose the RS485 method (via PLC Program Port) to connect S7-200 and HMI DOP-B.
Set the connection parameters on software
The connection parameters for connect PLC and HMI:
- Interface: RS485, RS232, Ethernet…
- COM port: COM1, COM2…
- Baud rate: 9.6 kbps, 19.2 kbps, 187.5 kbps…
- Data Bits: 7 bits, 8 bits
- Stop Bits: 1 bit, 2 bits
- Parity: Even, Odd…
- Station Controller Address
- Timeout, Retry Count, Delay time…
On Programmable Software of HMI
With the HMI Programs, the option name to set the connection parameters is different. Ex: With Delta, DOPSoft program is “Communication setting”. In normal, the default setting is ok (one HMI – one PLC).
On Programmable Software of PLC
With the PLC Programs, the option name to set the connection parameters is different too. Ex: With Siemens Step7 MicroWIN V4.0 program is “Communication port” in System Block. With the PLC Program, you make the parameters same with HMI Program above for connect PLC and HMI.
S7-200 processes a longer period of internal program scanning or inputs an interruption command may slows down HMI response rate and cause “Must Retry” or “No Such Resource” error message. The communication Delay function is suggested to avoid this problem. The parameter setting unit is ms and suggested setting value is 10. The setting value should not be greater than 30 (By: “DOP Series HMI Connection Manual”).
The video guide connect PLC and HMI (S7-200 PLC and Delta HMI)
In the next post, I will show you: How to make the PLC & HMI connection cable.
If you find this content valuable, please rate it (click the button above), share it with your friends or invite me for a coffee by clicking the button below.